PLEASE BE SURE YOUR QUOTE INCLUDES THE
FOLLOWING INFORMATION, AS APPLICABLE.
COMPLETED QUOTATION REQUEST FORM
Your Company Name and Address at the Top of Quotation Request form
Manufacturer and Part Number(s)
(Either included in total price or itemized separately.)
All Quotes are F.O.B. Redding, CA.
Sales Tax (7.25% for product purchases)
Completed Acknowledgment of any Addenda issued
Addenda (if any issued) will be posted on our website
Completed Signature Portion of Quotation Request form
The City of Redding does not accept
This form must be hand signed.
Quotes May Be Sent Via
Email ( Quotes@cityofredding.org )
Fax (530) 225-4434
U.S. Mail / Hand Deliver To:
Purchasing Division, 3rd Floor
City of Redding
777 Cypress Avenue, Redding CA
EMAIL SUBJECT LINE SHALL BE CLEARLY MARKED WITH THE RFQ NUMBER & TITLE
FOR SECURITY PURPOSES,
EMAILS NOT APPROPRIATELY IDENTIFIED MAY NOT BE OPENED.
QUOTES MUST BE RECEIVED BY THE DUE DATE AND TIME
INDICATED ON THE QUOTATION REQUEST FORM
THE CITY OF REDDING IS NOT RESPONSIBLE FOR RECEIPT OF VENDOR=S QUOTATION.
25' or 35'
(AS INDICATED ON DRAWINGS)
SINGLE ARM POLE
DOUBLE ARM POLE
Tapered aluminum standard shall be designed to withstand 85 m.p.h. wind speed, and exposure Category C
in accordance with AASHTO Standard Specifications for Structural Supports for Highway Signs, Luminaires,
and Traffic Signs. Each light standard shall include: 2" tubular support arm 6' reach, 25' or 35' fixture height,
anchor bolts covers, shaft cap, and a 4" x 6.5" hand hole with flush mount cover located 90° from arm
centerline. (See sketch).
APPROVED FOR PURCHASE:
25' SINGLE ARM POLE (25')
LEXINGTON (SEE NOTE 6)
21-295 2208 - 40705T4 W/1 MA0632B40 ARMS RTA04-100
2208 - 45805T4 W/1 MA0632B45 ARMS
25' DOUBLE ARM POLE (25') 22-295 2208 - 45805T4 W/2MA0632B45 ARMS RTA16-100 150-Y25 E690.22
35' SINGLE ARM POLE (35') 21-865 3208 - 45805T4 W/1 MA0632B45 ARMS RTA10-100 150-Y22 E690.36
35' DOUBLE ARM POLE (35') 22-885 3208 - 45805T4 W/2MA0632B45 ARMS RTA22-100 150-Y27 E690.35
NOTE: Associated material i.e., arm, bolts covers, anchor bolts, etc., may be specified separately.
1-HOLE, 2-WIRE MECHANICAL LUG
FOR USE WITH #1 /0-#14 AUCU
CONDUCTOR; ILSCO AU-0 OR
EQUAL. (SEE NOTE 5) ---+---+-I-
LOOKING INTO HANDHOLE
1. Wire from luminaire to base shall be
nonmetallic sheathed cable type UF-B,
3 #14 (2 #14 + #14G) copper, 600 volt
2. Wire from base to point of service shall
be 2 #6 + #6G, aluminum, type USE-2
(See Public Works Standard Page
510), or as indicated on the drawings.
3. REU will make connections at base of
light pole and any applicable
supply-side splicing locations.
4. Must state single or double arms on
5. Customer shall furnish and install
mechanical ground lug and make
connection of ground wire from
Redding Electric Utility
SHEET 1 OF2
ELECTRIC CONSTRUCTION STANDARD
ALUMINUM STREET LIGHT STANDARD
POLE AND ARM DETAILS